12 New 660-Wg Light Switch Wiring Images
Galleries photos in this diagram:
Other recommended photos you might like:
How To Replace A Light Switch - In case you want to add a 2d, new receptacle beneath this switch and you run a new 14/2 from this switch field to feed the new receptacle below you have a hassle; there's no impartial at this transfer box. You would must feed your new receptacle from the first one proven right here, even though it's far 10 ft away.
Electrical cutting-edge starts at l1 and flows through the black twine to the pink wire nut connection #1 inside the light field. Cutting-edge then flows thru the white cord this is marked with black tape (not a neutral) to terminal #2 on the single pole transfer. Inside the transfer, after the transfer blade is closed, contemporary flows through the switch blade (purple) from terminal#2 to terminal #3. It then leaves #three and follows the black “transfer leg” cord to the purple wire nut connection #four inside the mild field after which on to terminal#5 on the mild. From #5 current flows via the filament twine in the bulb and out to terminal #6. From there present day returns through the white neutral cord to purple wire nut connection #7 and returned to impartial, n.
Rating amazing a this method is typically used whilst 2 switches want to be in a unmarried gang place. Degree intermediate description energy is fed to the combo switch via pulling a2 twine feed from the closest source of energy. Then2 switch legs are pulled from the switch to a ceiling fan. Athree twine has 2 switch legs in it; a crimson for the light and a black for the fan with the white getting used as the neutral. If you have no three twine to be had you can pull 2 wires which would depart you with an additional white impartial. One black for the light the other black for the fan and one of the whites for the impartial. Take into account that those unmarried poles aren't 3ways or 4ways which means that the first s1 can't flip off the fan if the third s1 is in the on function. The fan is off when the disconnect transfer (transfer 1-2) is on and all three s1s are off (switches three-8, four-7 and five-6) the fan is on when the disconnect switch and any one or greater of the s1s also are on as proven right here;.